Cenergist upgraded the plant rooms of a local football stadium.
The heating and hot water for the main ground is supplied by 9 various gas boilers from Hamworthy to Hoval totalling around 6,000kW. In the first phase the largest 11 boilers were fitted with boiler management units and some 340 unwrapped fittings were insulated.
PAYBACK AND CO2 SAVINGS
• The boilers on the first phase were consuming 6.3 million kWh.
• The boiler management units produced savings of 16%, equating to 940,000kWh and 180,000 Kg of Co2.
• The flexible insulation installed saved a further 189,000kWh and 82,000kg of Co2.
• Payback for the boiler management units was five months and for the flexible insulation was 13 months.